Overview The wireless remote control valve uses the NB wireless module internally to remotely control the opening and closing of the ball valve, the upload frequency of the device, and whether the indoor temperature collector is allowed to control the opening and closing of the ball valve of the product. The product uses ST's low-power chip internally. The 3.7V lithium battery is powered, the sleep current is less than 5uA, and the internal lithium battery can keep the device working for more than 5 years. The wireless remote control valve is suitable for controlling non-corrosive gases or liquids. It is not suitable for use when the ball valve opening degree is often changed because the lithium battery used in the product is powered instead of the external power source.
Device parameters Operating voltage 3.7V sleep mode current less than 5uA working time Default time November - March (depending on district heating time) control mode user remote control via software, indoor temperature collector upload frequency (heating season) 1 – 127 hours Optional, default 24-hour control valve opening and closing degree 11 state adjustable connection method Pipe thread G nominal pressure 1.6Mpa
The remote control client software can remotely control the upload frequency of the device, whether to allow the indoor temperature collector to control, and the opening and closing of the ball valve. Adjustment period The device uploads the data in 10 minutes (that is, receives the data sent by the platform in ten minutes), which is convenient for the customer to demonstrate and adjust the ball valve. Intelligent Control In the case where the client software setting allows the indoor temperature collector to control the remote control ball valve, the user can control the remote control ball valve by setting the indoor temperature collector (see the indoor temperature collector manual for details).